Aqua Rite Replacement T-Cell 15K Gallon
T-CELL 3 & 9 are NOT compatible with systems built before 2009.
Open the Data Sheet in the Resource Center for instructions on finding your software revision
**** IMPORTANT ****If your system was built prior to 2009 you can use an OEM factory T-CELL-15 or CompuPool GRC40GH generic sizes.****
The Aqua Rite Replacement T-Cell 15K Gallon Turbo Cells automatically generate a self-renewing supply of fresh, pure chlorine for water that’s clean, clear and luxuriously soft. Turbo Cells come in three sizes for in-ground pools ” 40,000, 25,000 and 15,000 gallons. The three sizes enable you to right-size your salt system for the most efficient and cost-effective chlorination possible.
Aqua Rite Electronic Chlorine Generators (also known as salt chlorinators) are the largest selling system in the world. They automatically produce pure chlorine every day while the pool is being filtered and distribute it evenly throughout the pool via the return jets. Aqua Rite generators use a low concentration of salt dissolved in the pool water (below the level of taste) to produce up to 1.45 lbs of chlorine daily, enough for all residential pools up to 40,000 gallons. They are also NSF certified and approved for use on commercial and public pools. They easily install on standard filtration systems, both for new construction and on existing pools.
No more mixing, measuring and messing around with liquid or tablet chlorine. Aqua Rite automatically turns common salt into a self-regenerating supply of pure chlorine. For pool and spa water that’s clean, clear and luxuriously soft.
The key to Aqua Rite’s chlorine generation is the Turbo Cell®, a specially-designed converter connected to the control unit by a simple plug-in cord, and plumbed into the filter pump’s return line to the pool. As water is pushed through the Turbo Cell, an extremely safe low-voltage electrical charge turns the salt previously added to the water into fresh, sanitizing chlorine which is then dispersed evenly throughout the pool via the return jets.
Right-sized salt chlorination
Hayward now offers a new line of Turbo Cells for their salt chlorination and controls solutions. The cells come in three sizes ” 40,000, 25,000 and 15,000 gallons. The new sizes enable you to right-size your pool for the most efficient and cost-effective chlorination possible. These cells are based on the proven Turbo Cell technology that made Hayward the leader in salt chlorination. They automatically generate a self-renewing supply of fresh, pure chlorine ” for water that’s clean, clear and luxuriously soft.
Aqua Rite Replacement T-Cell 15K Gallon Features:
- Simple homeowner operation
- Adjust chlorine output from 1 to 100%
- The best water quality attainable
- Always crystal clear and ready for swimming
- Soft silky feel means no more red eyes or dry skin
- Microprocessor automates all functions
- Digital salt display and 8 diagnostic indicators
- Patented Turbo Cell for maximum efficiency and flow rates
- Super chlorinate function
- Automatically cleans the cell by periodically reversing the polarity
- Quick, weatherproof connections inside control door
- Single unit for 120VAC/240VAC 50/60 Hz power input
- Locking weatherproof enclosure
- UL and CUL Listed, NSF certified
Goldline AquaRite also-known-as Nature Soft Salt Systems
Maintaining the Aqua Rite System
To maintain maximum performance, it is recommended that you open and visually inspect the cell every 3 months or after cleaning your filter. The Aqua Rite® will remind you to do this by flashing the “Inspect Cell” LED after approximately 500 hours of operation. After you inspect the cell (and clean, if necessary) press the small “diagnostic” button next to the display for 3 seconds to stop the flashing “Inspect Cell” LED and start the timer for the next 500 hours.
The Aqua Rite electrolytic cell has a self-cleaning feature incorporated into the electronic control’s logic. In most cases, this self-cleaning action will keep the cell working at optimum efficiency. In areas where water is hard (high mineral content) and in pools where the water chemistry has been allowed to get “out of balance”, the cell may require periodic cleaning. The “Inspect Cell” LED will indicate if cell efficiency is decreased and servicing is necessary. If the “Inspect Cell” LED remains on after a thorough cleaning, the cell may be worn and require replacement.
Servicing and Cleaning the Aqua Rite Replacement T-Cell 15K Gallon
Turn off power to the Aqua Rite before removing the electrolytic cell. Once removed, look inside the cell and inspect for scale formation (light colored crusty or flaky deposits) on the plates and for any debris which has passed through the filter and caught on the plates. If no deposits are visible, reinstall. If deposits are seen, use a high-pressure garden hose and try to flush the scale off. If this is not successful, use a plastic or wood tool (do not use metal as this will scratch the coating off the plates) and scrape deposits off of plates. Note that a buildup on the cell indicates that there is an unusually high calcium level in the pool (old pool water is usually the cause). If this is not corrected, you may to have to periodically clean the cell. The simplest way to avoid this is to bring the pool chemistry to the recommended levels as specified.
Mild Acid Washing:
Use only in severe cases where flushing and scraping will not remove the majority of deposits. To acid wash, turn off power to Aqua Rite. Remove cell from piping. In a clean plastic container, mix a 4:1 solution of water to muriatic acid (one gallon of water to one quart of muriatic acid). ALWAYS ADD ACID TO WATER – NEVER ADD WATER TO ACID. Be sure to wear rubber gloves and appropriate eye protection. The level of the solution in the container should just reach the top of the cell so that the wire harness compartment is NOT submerged. It may be helpful to coil the wiring before immersing the cell. The cell should soak for a few minutes and then rinse with a high-pressure garden hose. If any deposits are still visible, repeat soaking and rinsing. Replace cell and inspect again periodically.
The Aqua Rite electrolytic cell and flow detection switch will be damaged by freezing water just as your pool plumbing would. In areas of the country which experience severe or extended periods of freezing temperatures, be sure to drain all water from the pump, filter, and supply and return lines before any freezing conditions occur. The electronic control is capable of withstanding any winter weather and should not be removed.